Description: The article discussed the problem of determining the response time control system for input actions. It was necessary to evaluate the response time of the system at the same time for a few dozen channels of input \ output. Such tests are carried out in accordance with IEC 61508, which is the basic document defining the rules for the creation of information-management systems for the management of hazardous process. To solve such a problem in the article it was suggested to use the software and hardware company National Instrument.
Keywords: validation, FPGA, IEC 61508, АСУ ТП, National Instrument, LabView